Top part flange made of rigid PVC
Top part flange collar made of bituminous membrane (PYE PV 200 S4 sanded surface)
Base flange made of rigid PVC
Base element flange collar made of bituminous membrane (PYE PV 200 S4 sanded surface)
Note (pay attention before placing the order!):
Before ordering, check whether the heating appliance has the necessary type test and installation type marking for the connection to the planned chimney. Appliance type C6 is required for room sealed operation. In case of multi inlet arrangements or cascades in positive pressure mode, the heating appliances must also be equipped in the factory or retrofitted with downdraught protection. The flue gas routing must be agreed with the authorised district chimney sweep before placing the order.
Please note that use of the product must be matched to the circumstances on site. We do not provide any guarantee that our information meets the requirements of the call for tenders/tender and can be used for the planned heating appliance. The suitability of the heating appliances must be checked, particularly in the case of cascades and multi inlet arrangements. The boiler manufacturer’s consent may be necessary.
When installing the horizontal flue gas passages please pay attention to adequate gradient to the boiler. According to DIN V 18160-1 § 6.10.04, a gradient of 3° must be maintained. The is equal to 5 cm per metre. Please follow the general installation instructions of ATEC (atec-abgas.de) for article 10003400.